E3S Web Conf.
Volume 10, 20161st International Conference on the Sustainable Energy and Environment Development (SEED 2016)
|Number of page(s)||4|
|Published online||17 October 2016|
ICCP cathodic protection of tanks with photovoltaic power supply
1 AGH University of Science and Technology, Department of Fossil Fuels, Krakow, Poland
2 AGH University of Science and Technology, Electrical Department, Krakow, Poland
a Corresponding author: firstname.lastname@example.org
Corrosion is the result of the electrochemical reaction between a metal or composite material usually having conducting current properties. Control of corrosion related defect is a very important problem for structural integrity in ground based structures. Cathodic protection (CP) is a technique to protect metallic structures against corrosion in an aqueous environment, it is employed intense on the steel drains in oil and gas industry, specifically to protect underground tanks and pipelines. CP is commonly applied to a coated structure to provide corrosion control to areas where the coating may be damaged. It may be applied to existing structures to prolong their life. There are two types of cathodic protection systems: sacrificial (galvanic) anode cathodic protection (SACP); the other system is Impressed Current Cathodic Protection (ICCP). Majority of the structures protected employ impressed current system. The main difference between the two is that SACP uses the galvanic anodes which are electrochemically more electronegative than the structure to be protected - the naturally occurring electrochemical potential difference between different metallic elements to provide protection; ICCP uses an external power source (electrical generator with D.C.) with inert anodes, and this system is used for larger structures, or where electrolyte resistivity is high and galvanic anodes cannot economically deliver enough current to provide protection. The essential of CP is based on two parameters, the evolution of the potential and the current of protection. A commonly accepted protection criterion used for steel is a potential value of minus 850 mV. ICCP system consist of anodes connected to a DC power source. As power sources may be used such as solar panels, wind turbines, etc. The object of this study is analysis of the possibilities and operating parameters of ICCP system supplied with photovoltaic solar panels. Photovoltaic generator made up of the following elements: photovoltaic modules of solar cells, a control and regulation system, a storage system.
© The Authors, published by EDP Sciences, 2016
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.