E3S Web Conf.
Volume 14, 2017Energy and Fuels 2016
|Number of page(s)||10|
|Published online||15 March 2017|
Simplified method for calculating SNCR system efficiency
Division of Boilers and Steam Generators, Institute of Power Engineering and Turbomachinery, Silesian University of Technology, Konarskiego 20, 44-100 Gliwice, Poland
* Corresponding author: firstname.lastname@example.org
SNCR (Selective Non-Catalytic Reduction) technology is aimed at reducing NOx emissions. SNCR efficiency is appropriately high only for the reaction temperature range called ‘the SNCR temperature window’. It is a narrow temperature range defined in various ways in the literature, which makes it difficult to evaluate the DeNOx system’s efficiency. Therefore, this study attempts to approximate the relationship between SNCR system efficiency and the flue gas temperature. The approximation was performed on the basis of literature data and verified using data from an experiment. Measurements were performed in a Polish boiler with a maximum continuous rating of 230 t/h. The verified, evaluated function could be used to forecast efficiency of SNCR systems in existing units that use urea or ammonia as a reagent. The approximation results are polynomial functions that depend on flue gas temperature, which fit the literature data with the coefficient of determination R2 = 0.83-0.86. Therefore, these equations could be used by the designer or operator of the boiler for preliminary determination of current SNCR system efficiency.
© The Authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.