E3S Web Conf.
Volume 35, 2018Scientific-Research Cooperation between Vietnam and Poland (POL-VIET 2017)
|Number of page(s)||7|
|Published online||23 March 2018|
Research for Forming up the Controlling Diagram Utilizing the Connection of a LV Resistor on Voltage Transformer’s Open-Triagle Coil to Reduce over Voltage Caused by Earth Fault in 6 kV Grid of QuangNinh Underground Mines
Department of Electrification, Electromechanic Faculty, Hanoi University of Mining and Geology, Viet Nam
* Corresponding author: email@example.com
Single phase earth-fault in MV grids usually causes overvoltage that harm to human being and electric equipment. If the magnitude of over voltage is so great, many grids’ eco-technical parameters will be affected. The paper analyzes all possible consequences of over voltage occurred in 6 kV grid of QuangNinh underground mines. Base on the analysis, a controlling diagram utilizing the connection of a LV resistor on voltage transformer’s open-triangle coil to reduce over voltage is recommended. The simulation results of the diagram are used to prove the effectiveness of solution: the over voltage magnitude is only in the range of (2,1–2,4).Uf. Other advantage that solution brings to relay system will be pointed out.
Key words: earth fault / over voltage / open-triangle coil / 6 kV grid
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited. (http://creativecommons.org/licenses/by/4.0/).
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.