E3S Web Conf.
Volume 44, 201810th Conference on Interdisciplinary Problems in Environmental Protection and Engineering EKO-DOK 2018
|Number of page(s)||8|
|Published online||03 July 2018|
The slotted – displacement ceiling diffuser as an alternative to the organization of down – up air exchange in rooms with computer equipment
Wroclaw University of Science and Technology, Faculty of Environmental Engineering, Department of Air Conditioning, Heating, Gas Engineering and Air Protection, 4/6 Norwida st. 50-373 Wroclaw, Poland
* Corresponding author: firstname.lastname@example.org
The article analyses heat loads occurring in public utility rooms with computer or multimedia equipment. Attention has been paid to the possibility of using down – up type (displacement ventilation, DV) and up – up type (mixing ventilation, MV) of air exchange. The design of the slotted – displacement ceiling diffuser is presented. The results of measurements in non-isothermal conditions in the form of air flows in the area of its operation are provided. The graphs show the graphical distribution of velocities and air temperatures in the vertical plane passing through the transverse axis of the special diffuser. The study of the behavior of the stream flowing out of the diffuser was only in the scope of work. The velocity and air temperature distribution over the heat sources, which were located away from the diffuser, next to the external walls, was not studied. The focus was on three representative airflows of supply air and the behaviour of the air stream during cooling was presented.
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.