E3S Web Conf.
Volume 111, 2019CLIMA 2019 Congress
|Number of page(s)||6|
|Section||Advanced HVAC&R&S Technology|
|Published online||13 August 2019|
The evaluation of energy saving performance for the modular design centrifugal chiller
1 Air Solution Laboratory, LG Electronics Inc., 150-802, Seoul, Korea
2 Air Solution Business Unit, LG Electronics Inc., 642-713, Changwon City, Korea
* Corresponding author: firstname.lastname@example.org
The modular concept design and operation of a centrifugal chiller offers the potential of increased cycle efficiency both at full load and off load conditions compared to the single compressor chiller. Modular chiller design is that a smaller, individual chiller can be connected with another, to make a larger capacity system. In the case of a tandem chiller, there would be faced to the higher initial cost or bigger foot print than a single compressor chiller at the same capacity because manufacturing cost, weight and size will be decreased according to increase of the refrigeration capacity. Therefore, it is obvious that a modular chiller have to be improved its efficiency first by both the operation algorithm and major cycle components. Eventually, the efficiency of the modular chiller achieves up to 6% at the full load condition after added series counter flow effect as much as 3% and more 3% added by improved aerodynamic design for impeller. Moreover, maximize off design potential through the capacity combination algorithm as the way of uneven loading makes 24% improved based on AHRI 550/590.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.