E3S Web Conf.
Volume 136, 20192019 International Conference on Building Energy Conservation, Thermal Safety and Environmental Pollution Control (ICBTE 2019)
|Number of page(s)||4|
|Section||Integrated Application of Renewable Energy in Buildings|
|Published online||10 December 2019|
Analysis of movable guide vane inversion and limited block dropping of hydropower plants
1 Hunan Electric Power Research &Test Institute, Changsha, Hunan, 41007, China
2 State Grid Hunan Transmission Maintenance, Changsha, Hunan, 41007, China
* Corresponding author’s e-mail:firstname.lastname@example.org
The fracture signal of shear pin occurs in the process of short time load reduction of AGC. During the stop site inspection, it is found that the shear pin was broken, the guide vane limit block fell off, and the movable guide vane was reversed. The analysis shows that the installation and welding mode of the limited block is wrong. Therefore, when the guide vane is subjected to additional load, the position of the fixed guide vane cannot be effectively limited, which leads to the inversion of the fixed guide vane.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.