E3S Web Conf.
Volume 185, 20202020 International Conference on Energy, Environment and Bioengineering (ICEEB 2020)
|Number of page(s)||6|
|Section||Energy Engineering and Power System|
|Published online||01 September 2020|
Modelling& Simulation and Protection& Control Verification Method for Asynchronous Motor-Synchronous Generator Sets
China Electric Power Research Institute, Beijing, 100192, China
* Corresponding author’s e-mail: email@example.com
Power supply system made of asynchronous motor-synchronous generator sets (M-G sets) is often used as power supply for important loads. The system usually consists of two M-G sets. Unlike synchronous generators connecting to large power grid, the two generators in the system can have significant effect on the other when field loss fault occurs. If the protection settings are inappropriate, the two generators may trip one after another during a fault on a single generator, causing the important load losing all the power supply. This paper proposed a simulation and protection verification method based on the RTDS digital modelling for M- G sets including detailed excitation system. The modelling and simulation methods can effectively verify the reasonability of settings of the P-Q restriction of the excitation regulator and the PID controllers, and provide the important basis for the setting of over-current protection and loss of excitation protection, ensuring the safe operation of the power supply system made of M-G sets.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.