E3S Web Conf.
Volume 22, 2017International Conference on Advances in Energy Systems and Environmental Engineering (ASEE17)
|Number of page(s)||8|
|Published online||07 November 2017|
Preliminary sanitary analysis of supply and exhaust air of ventilation units working at special rooms
Wydział Inżynierii Środowiska, Politechnika Wrocławska, Wyb. Wyspiańskiego 27, 50-370 Wrocław, Poland
* Corresponding author: email@example.com, firstname.lastname@example.org
This article is an attempt to estimate concentration of bacteria and fungi in characteristic places in two air handling units. The research was conducted with the units equipped with heat recovery exchanger and recirculation of exhaust air. Additionally, microbiological analysis was done for indoor and fresh air. We performed measurements regarding supply and exhaust air volume. This means that the air velocity inside ventilator chamber was known. The mean concentration of bacteria and fungi was specified for air filters on the supply and exhaust side. The efficiency of air filters was verified by the concertation of bacteria and fungi in fan chamber. This article confirms that bacteria content in supply air is always lower than in exhaust air despite air recirculation. In this work we proved that the position of Petrie plate is essential for bacteria and fungi measurement.
© The Authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited. (http://creativecommons.org/licenses/by/4.0/).
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.