E3S Web Conf.
Volume 25, 2017Methodological Problems in Reliability Study of Large Energy Systems (RSES 2017)
|Number of page(s)||4|
|Section||Reliability problems of energy systems and the practice of their solution|
|Published online||01 December 2017|
Effect of duration of the pause single-phase auto-reclosing on electro-power transmission capacitance
Novosibirsk State Technical University, 630073, Novosibirsk, Russian Federation
* Corresponding author: firstname.lastname@example.org
This paper discusses the problem associated with accidents in the aerial line (AL) ultra-high voltage (UHV) due to its big length. In lines with a voltage of 500-1150 kV the overwhelming proportion of trips (98%) is caused by single-phase short circuit (SPSC). A substantial portion (70%) single-phase short circuits is erratic arc accidents which can be successfully eliminated in a high-speed auto-reclosing (HSAR) or single-phase auto-reclosing (SPAR). Success single-phase auto-reclosing (SPAR) at liquidation by single-phase short circuit (SPSC), on the one hand, is determined by the characteristics of the secondary arc current, and on the other hand the effectiveness of ways to reduce secondary arc current and recovery voltage development. The minimum dead time, at a HSAR it is usually taken as 0.5 s., at single-phase autoreclosing (SPAR) it depends on the current value of the arc support is in the range of 0.5-3.0 s. The article shows high efficiency of use single-phase auto reclosing (SPAR) at liquidation SPSC in a single-chain AL voltage of 500 kV, the dependence of the bandwidth of transmission in maintaining the dynamic stability from the length of the pause SPAR.
© The Authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited. (http://creativecommons.org/licenses/by/4.0/).
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.