E3S Web Conf.
Volume 111, 2019CLIMA 2019 Congress
|Number of page(s)||8|
|Section||Advanced HVAC&R&S Technology|
|Published online||13 August 2019|
A laboratory apparatus to study Thermal Response Test in the presence of groundwater flow
Politecnico di Milano, Energy Department, v. Lambruschini 4, 20156, Milano, Italy
* Corresponding author: email@example.com
The standard approach to Thermal Response Test, based on conduction heat transfer in the ground, turns out to be unsuccessful under significant groundwater flow. The applicability of the Moving Infinite Line Source model to interpret the TRT in this case still needs to be proved. In order to study the TRT in the presence of a groundwater flow, an original laboratory apparatus has been developed. The Sand Box design is based on a heat transfer similitude between the real scale TRT problem and the laboratory scale one. The Sand Box sizes (1,2 m x 0.6 m x 1.0 m) are then set in order to keep the boundaries unaffected by the heat source during the TRT. The U-pipe heat exchanger is reproduced through a twocables electrical resistance 1 m long. A hydraulic loop with a peristaltic pump allows to obtain a Darcy velocity across the sandy soil up to 6,7510-5 m/s. The measurement system consists in several thermocouples in the porous medium and in a flow meter. The TRT results at null groundwater velocity allow to derive a reference thermal conductivity. The first tests with groundwater flow show the suitability of the apparatus and allow to derive some preliminary considerations.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.