E3S Web Conf.
Volume 111, 2019CLIMA 2019 Congress
|Number of page(s)||6|
|Section||High Energy Performance and Sustainable Buildings|
|Published online||13 August 2019|
Radiant wall cooling with pipes arranged in insulation panels attached to facades of existing buildings
1 Slovak University of Technology, Faculty of Civil Engineering, Radlinského 11, 810 05, Bratislava, Slovakia
2 Brno University of Technology, Faculty of Civil Engineering, Veveří 331/95, 602 00, Brno, Czech Republic
* Corresponding author: email@example.com
Radiant systems are being increasingly used for space heating and cooling of buildings. The contemporary research of radiant systems addresses mainly floor and ceiling structures. Research regarding the possibilities of their incorporation in wall structures is lacking, despite their potential advantages. This study addresses a radiant wall system manufactured according to a patent. The patented design involves panels that consist of pipes arranged in milled channels in thermal insulation. The potential advantage of this system is the fact that the thermally active panels can be attached to the facades of existing buildings as a part of their retrofit. Thereby, only minor interventions on the interior side of the retrofitted buildings are needed. To test and improve the design of the wall system, laboratory measurements and computer simulations were performed on a wall fragment for its operation under summer conditions. The results indicate a significant potential for improvement of the patented design by addressing the imperfections in the contact between pipe and wall. Inserting a metal fin between pipe and wall enhanced the cool distribution within the wall fragment considerably. From the three materials of the metal fin considered, using copper led to highest values of the cooling output, followed by aluminium. For these two metals the effect of increasing the thickness of the fin on the cooling output was small. On the contrary, the fin made of steel was the least efficient in terms of cool distribution. In this case the cooling output was most sensitive to the thickness of the fin.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.