E3S Web Conf.
Volume 152, 20202019 International Conference on Power, Energy and Electrical Engineering (PEEE 2019)
|Number of page(s)||6|
|Section||Power Electronics and Transmission Technology|
|Published online||14 February 2020|
Effect of measuring distance error on working phase voltage at zero potential live working point
Hunan transmission Maintenance Company, Changsha 410100, China
2 Live Inspection and Intelligent Operation Technology State Grid Corporation Laboratory, Changsha 410100, China.
* Corresponding author: firstname.lastname@example.org
When the live working is carried out in the distribution network, the zero-potential charging operation is often used. The safety of zero-potential live working is closely related to the measurement distance error. The influence of the measurement error of the zero-potential live working point on the operating phase voltage needs to be studied. Based on the Floyd algorithm, a method for calculating the shortest electrical distance from the operating point to the substation is proposed. The sub-station is centered on the branch nodes of the line to form the distance matrix, and the Floyd algorithm is used to calculate the shortest electrical distance from the working point to the substation. The working phase injection voltage is further calculated based on the zero phase potential characteristics of the operating phase. Finally, based on the PSCAD, the system model is established. The simulation concludes that the distance between the substation and the working point is less than 20m, and the operating point voltage can still be below the safe voltage.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.