E3S Web Conf.
Volume 216, 2020Rudenko International Conference “Methodological problems in reliability study of large energy systems” (RSES 2020)
|Number of page(s)||3|
|Published online||14 December 2020|
Method for the diagnosis of high-voltage dielectric elements during operation based on dynamic registration of electromagnetic radiation
1 Kazan State Power Engineering University, Russia
* Corresponding author: firstname.lastname@example.org
Complex remote monitoring and the developed non-contact diagnostic device (NDD) allow monitoring the technical condition and revealing the residual life of high-voltage dielectric elements. It is based on non-contact remote periodic measurement of a set of diagnostic parameters (characteristics of electrical discharges emitted by insulators during operation) necessary for a reliable assessment of the operating state of high-voltage dielectric equipment at the moment of operation and determination of its residual life. NDDs are installed on each phase conductor and used to measure diagnostic parameters, followed by computer processing of the accumulated information signals. An analysis of the set of necessary diagnostic parameters makes it possible to form a conclusion on the degree of performance of dielectric elements. The paper considers a method for detecting defective high-voltage insulators using the developed non-contact diagnostic devices by the radio frequency method and assessing the difference in time of arrival of a partial discharge signal.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.