E3S Web of Conf.
Volume 216, 2020Rudenko International Conference “Methodological problems in reliability study of large energy systems” (RSES 2020)
|Number of page(s)||4|
|Published online||14 December 2020|
Analysis of small oscillations of complex electrical systems
1 Tashkent State Technical University named after Islam Karimov, Power Plants, Networks and Systems Department, Universitetskaya 2, Tashkent, 100095, Uzbekistan
2 Tashkent State Technical University named after Islam Karimov, Power Plants, Networks and Systems Department, Universitetskaya 2, Tashkent, 100095, Uzbekistan
The article discusses the results of the analysis of the static stability of complex electrical systems. The efficiency of the combined application of the equations of nodal voltages (ENV) and the Lyapunov function in quadratic form for the analysis of small oscillations of the electrical system is shown in the literature, which is called the Allaev method. A joint solution of the equations of nodal voltages and the matrix Lyapunov equation is given, which makes it possible to determine the stability conditions for the electrical system and identify the generator first approaching the stability limit. A study of small oscillations of complex electrical systems, which can be performed in full on the basis of matrix methods, successfully developed in recent decades, is carried out, which is associated with a sharp increase in the speed of computation and the amount of memory of modern computers.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.