E3S Web Conf.
Volume 252, 20212021 International Conference on Power Grid System and Green Energy (PGSGE 2021)
|Number of page(s)||4|
|Section||Power Control Technology and Smart Grid Application|
|Published online||23 April 2021|
Research on Defect Detection Technology of Composite Insulator Sheath
1 State grid hunan electric power company limited research institute, Changsha, Hunan, 410007, China
2 State Grid Hunan Transmission Maintenance, Changsha, Hunan, 410000, China
3 State grid hunan electric power company limited, Changsha, Hunan, 410000, China
* Corresponding author’s e-mail: email@example.com
The composite insulator sheath plays an important role in protecting the core rod and insulation. The thickness of the sheath must meet the corresponding standard requirements. During the insulator manufacturing process, the core rod decentration leads to uneven thickness of the sheath, which is easy to cause the risk of composite insulators premature failure during operation. The phased array detection technology can accurately detect the thickness of the sheath, so that defects such as uneven thickness of the sheath (decentration of the core rod) can be detected, and the thickness of the sheath at the end of the composite insulator can also be effectively detected. DR detection technology can effectively identify the interface between the mandrel and the sheath, but there is a risk of the sheath thickness distortion due to inappropriate transillumination parameters.
© The Authors, published by EDP Sciences, 2021
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.