E3S Web Conf.
Volume 252, 20212021 International Conference on Power Grid System and Green Energy (PGSGE 2021)
|Number of page(s)||11|
|Section||Research and Development of Electrical Equipment and Energy Nuclear Power Devices|
|Published online||23 April 2021|
State Evaluation Model of High voltage Switchgear Based on Fuzzy Set-valued Statistical Method and Kernel Vector Space Model
1 State Grid Tianfu Power Supply Company, Chengdu 610041, China
2 College of Electric Engineering, Sichuan University, Chengdu 610065, China
* Corresponding author’s e-mail: firstname.lastname@example.org
The traditional high voltage switchgear (HVS) state evaluation model mostly adopts electrical test, live detection and historical data, neglecting the influence of real-time operation data of HVS composition equipment on the state evaluation results. This paper proposes a HVS operation state evaluation model based on fuzzy set-valued statistics method and kernel vector space model based on electrical test data and on-line monitoring data. First of all, according to the components of high voltage switchgear, the operation state of HVS is described and the evaluation index system is established. Secondly, the fuzzy set-valued statistics method is used to construct the mathematical model of evaluation index weight. Then, the kernel vector space model is introduced, and the Gaussian kernel function is used to map the sample to the features of the high-dimensional feature space. The indicator vector of the sample data and the ideal indicator vector of the high-voltage switchgear operation status level standard are defined in the high-dimensional feature space, and the angle-weighted cosine between the two vectors is calculated as the closeness of the sample to the standard status level, and then the high-voltage switchgear operation status level is obtained. Finally, the real data of a power supply company in western China are simulated. The results show that the greater the closeness degree is, the closer the HVS corresponding to the sample is to the normal state, on the contrary, the smaller the closeness degree is, the closer the HVS is to the fault state.
© The Authors, published by EDP Sciences, 2021
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.