E3S Web Conf.
Volume 252, 20212021 International Conference on Power Grid System and Green Energy (PGSGE 2021)
|Number of page(s)||4|
|Section||Research and Development of Electrical Equipment and Energy Nuclear Power Devices|
|Published online||23 April 2021|
Sequence component direction element based on power frequency variation
The State Grid Liaocheng Power Supply Company, Liaocheng 252000, China
* Corresponding author: email@example.com
Unlike the relatively stable network structure of the transmission and distribution network, under the new distribution network, resulting in errors in the impedance tuning of the fault directional element, misjudgment of the fault directional element, and a decrease in sensitivity. For this reason, this paper proposes a sequence component adaptive fault directional element based on power frequency variation. The sequence impedance amplitude is calculated through the measured values of the voltage sequence component and the current sequence component of the relay location. Then the phase angle of the setting impedance is determined according to various sequence components in the system. It improves the problem that the setting impedance of power frequency distance directional element is greatly affected by the amplitude and phase angle fluctuation of distribution system impedance and line impedance. The reliability and stability of the sequence component adaptive fault directional element based on the power fresquency variation are verified by Matlab simulation.
© The Authors, published by EDP Sciences, 2021
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.