E3S Web Conf.
Volume 252, 20212021 International Conference on Power Grid System and Green Energy (PGSGE 2021)
|Number of page(s)||6|
|Section||Energy Technology Research and Development and Green Energy-Saving Applications|
|Published online||23 April 2021|
Design a project of sewage plant to make the cross-section water quality reach standard
1 School of municipal and environmental engineering, Shenyang Jianzhu University, Shenyang, Liaoning Province, 110168, China
2 School of municipal and environmental engineering, Shenyang Jianzhu University, Shenyang, Liaoning Province, 110168, China
3 Tangshan Planning and Architectural Design & Research Institute, Tangshan, Hebei Province, 063000, China
4 School of municipal and environmental engineering, Shenyang Jianzhu University, Shenyang, Liaoning Province, 110168, China
According to regulations, the cross-section of Wangjiawopeng is regarded as a national control section of the Daling River. The water quality of the section must meet the surface water level III standard. According to the survey, the total phosphorus in the effluent from the sewage plant in Jianchang exceeds the standard is the main reason for the failure of the water quality. In order to make the cross-section water quality reaching standard, it is necessary to carry out the advanced treatment of phosphorus in the sewage plant. (1) The precipitation reaction of phosphorus and coagulant in sewage is strengthened by optimizing the type of coagulant, optimizing the dosage of coagulant, and selecting suitable coagulant aids. (2) The removal efficiency of phosphorus is improved by high-speed fiber filtration technology. (3) Phosphorus is removed by flocculation-sedimentation-high-speed fiber filtration technology. Experiments show that the SS in the sewage plant effluent is less than 5mg/L and filter effluent TP is less than 0.2mg/L. The process construction investment is estimated to be 3.9 million yuan, and the operating electricity cost is estimated to be 0.2 cents/m3. The process has the characteristics of reliable processing technology, stable operation, easy maintenance.
© The Authors, published by EDP Sciences, 2021
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.