E3S Web of Conferences
Volume 44, 201810th Conference on Interdisciplinary Problems in Environmental Protection and Engineering EKO-DOK 2018
|Number of page(s)||7|
|Published online||03 July 2018|
Experimental based determination of SCOP coefficient for ground-water heat pump
Department of Mechanical Engineering, Opole University of Technology, Mikołajczyka 5, 45-271 Opole, Poland
* Corresponding author: email@example.com
The paper presents research related to the operation of an ground-source heat pump with a thermal output of 16.85 kW and an electrical power of 3.72 kW in various conditions, both from the mechanical and thermodynamic perspective. The publication contains the results of research on a selected heat pump model with an R410a refrigerant carried out in an accredited laboratory in the Czech Republic. Detailed analysis of the data in terms of changes in the COP coefficient for two heating water temperatures was carried out (35°C and 55°C) and in the range of outdoor air temperature from -10°C to 15°C every 1°C. The analysis was also carried out to determine the efficiency of the heat pump depending on the parameters of the heat source. Devices of this type, enabling effective use of environmental available thermal energy with low operating costs, meet increasingly stringent environmental protection requirements. Significant costs of heating buildings are one of the main reasons for the need to look for alternative energy sources. The heat resources contained in water, air and land are huge. Due to the fact that heat pump prices dropped significantly, and their efficiency has increased over the last few years, these devices are a real competition for conventional ways of supplying buildings with heat. Heat pumps do not require daily maintenance, are fully automated and have intuitive control. These features allow to use them as components in the system of a modern and intelligent household. It was shown that the SCOP of the tested device increased by 1% on average reaching SCOP = 4.71 for a typical external calculation temperature and for a low-temperature heating system (35°C).
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.