E3S Web of Conferences
Volume 44, 201810th Conference on Interdisciplinary Problems in Environmental Protection and Engineering EKO-DOK 2018
|Number of page(s)||8|
|Published online||03 July 2018|
Reducing energy consumption of air-conditioning systems in moderate climates by applying indirect evaporative cooling
Department of Environmental Engineering, Wroclaw University of Science and Technology, 27 Wyspiański st., 50-370, Wroclaw, Republic of Poland
* Corresponding author: firstname.lastname@example.org
This paper investigates the potential of applying an indirect evaporative cooler for heat recovery in air conditioning systems in moderate climates. The counter-flow indirect evaporative heat and mass exchanger is compared with commonly used recuperation unit in terms of achieved energy. The performance analysis of the indirect evaporative exchanger is carried out with original ε-NTU-model considering condensation from treated air. It was found that the indirect evaporative exchanger employed as a heat recovery device, allows to obtain higher performance than conventional recuperator. Additional energy savings potential is related with utilizing the potential of water evaporation to pre-cool the outdoor air. It is also stated that there is a high potential of reusing condensate that forms in product channels of the indirect evaporative exchanger and in the vapour-compression unit and delivering it to the working part of the indirect evaporative exchanger.
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.