E3S Web of Conferences
Volume 44, 201810th Conference on Interdisciplinary Problems in Environmental Protection and Engineering EKO-DOK 2018
|Number of page(s)||8|
|Published online||03 July 2018|
The distribution of air temperature and velocity in the selected boiler room
Lodz University of Technology, Faculty of Architecture, Civil and Environmental Engineering, Al. Politechniki 6, 90-924 Łódź, Poland
* Corresponding author: email@example.com
The crucial impact on the indoor air quality in technological rooms, including boiler plant buildings, is made by operation of technological devices and ventilation systems. Therefore, the distribution of air temperature and velocity in these rooms mainly depends on location and heat gains generated by combustion devices, as well as emplacement of air supply and air exhaust elements. The temperature and airflow volume of supplied air is also an issue, because the indoor environment parameters are formed by the flow of air in the working area. Determination of the impact of physical factors on the thermal environment in a room is possible using an analysis of the air temperature and velocity. This issue is vital in terms of necessity to maintain the adequate heat conditions in the working area. Therefore, basing on the experimental measurements and numerical calculations (made in DesignBuilder software), the distribution of air temperature and velocity was analyzed in the selected industrial boiler room, located in the Lodz city, in Poland. The results obtained were compared with the recommended and limit values in the industrial buildings.
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.