E3S Web Conf.
Volume 113, 2019SUPEHR19 SUstainable PolyEnergy generation and HaRvesting Volume 1
|Number of page(s)||7|
|Section||Thermal and Electrical Hybrid Systems|
|Published online||21 August 2019|
Dynamic Effect of Cold-Air Bypass Valve for Compressor Surge Recovery and Prevention in Fuel Cell Gas Turbine Hybrid Systems
Thermochemical Power Group (TPG), University of Genoa, Via Montallegro 1, 16145 Genova, Italy
2 National Energy Technology Laboratory, Department of Energy, Morgantown, 26507 WV, USA
* Corresponding author: firstname.lastname@example.org
A large volume between compressor and turbine is present in fuel cell gas turbine hybrid systems. The substantially larger compressor plenum volume modifies the dynamic behaviour of these systems, increasing the risk of compressor surge during transients and subsequent destruction of both turbomachinery and fuel cell components. Diverting part of the compressor inlet flow directly to the turbine inlet through a cold-air bypass valve, bypassing the fuel cell stack, has been proven to be an effective method to increase the surge margin during normal operation and also to recover the machine from fully developed surge. This study investigates the dynamic effect of different cold-air bypass valve opening/closing procedures, especially steps and ramps changing the valve fractional opening. This analysis was carried out with reference to the Hybrid Performance (Hyper) facility: a hybrid system emulated using hardware and a cyber-physical fuel cell system at the National Energy Technology Laboratory (NETL), U.S. Department of Energy (DOE). Simulations performed on a Matlab®-Simulink® dynamic model of the system based on Greitzer’s theory showed a different behaviour varying the valve fractional opening with steps or ramps. Many experimental tests were performed on the Hyper facility to confirm the trends obtained from the simulations results. From the outcomes of this study, it has been possible to determine how to maximize the surge recovery effect of the cold-air bypass valve opening and to minimize surge related risks during the valve closure.
© The Authors, published by EDP Sciences, 2019
This is an open access article distributed under the terms of the Creative Commons Attribution License 4.0 (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.