E3S Web Conf.
Volume 124, 2019International Scientific and Technical Conference Smart Energy Systems 2019 (SES-2019)
|Number of page(s)||4|
|Section||Energy Systems and Complexes|
|Published online||25 October 2019|
Differential method for damage location determining in 10 kV distribution networks with isolated neutral
Kazan State Power Engineering University, Kazan, Russia
2 Kazan National Research Technological University, Kazan, Russia
* Corresponding author: Kirzhatskikh.firstname.lastname@example.org
Half of the length of all transmission lines (TL) are medium voltage networks. Single-line-to-ground short circuit (SLGSC) in distribution networks is the most common type of damage, accounting up to 70% of all types of damage. Faults in damage repair leads to an overvoltage of two healthy phases, resulting in double shorts, two-, three-phase shorts, which contributes to consumers’ disconnection. Remote damage location (DL) determination in tree-type networks is considered to be the most relevant, since these networks are spread over large areas, crossing rivers, ravines, lakes, forests, etc. This paper presents a differential method for DL determining based on steady-state voltage of damaged phase frequency. Measuring the parameters of emergency mode at the beginning and at the ends of 10kV TL allows compact stand-alone sensors using without their synchronization.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.