E3S Web Conf.
Volume 165, 20202020 2nd International Conference on Civil Architecture and Energy Science (CAES 2020)
|Number of page(s)||4|
|Section||Electrical and Power Engineering|
|Published online||01 May 2020|
Failure Analysis of Clamp Crack on TA Equipment in Converter Station
1 State Grid Hunan Electric Power Company Limited Research Institute, Changsha 410007, China
2 Hunan Xiangdian Boiler Pressure Inspection Center Co., Ltd, Changsha 410007, China
3 State Grid Hunan Electric Power Company Limited Yueyang Power Supply Company, Changsha 414100, China
4 State Grid Hunan Electric Power Company Limited Maintenance Company Changsha 410004, China
* Corresponding author: firstname.lastname@example.org
Through macro inspection, chemical composition analysis, hardness test, tensile performance test, microstructure inspection and scanning electron microscope analysis, the causes of clamp crack on TA equipment in the 500kV AC filter field of the ± 800kV converter station were analyzed. The results show that improper selection of the manufacturing process of the equipment clamps will cause more micro-defects inside it, leading to poor mechanical properties and excessive internal stress, which are the main causes of cracking. Corresponding measures are put forward to improve the manufacturing quality of equipment clamps, which can avoid similar failures from happening again.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.