E3S Web Conf.
Volume 288, 2021International Symposium “Sustainable Energy and Power Engineering 2021” (SUSE-2021)
|Number of page(s)||5|
|Published online||14 July 2021|
Analysis of distance protection’s operation in cases of deep saturation of current transformers
1 Novosibirsk State Technical University, K.Marksa prospect, 20, 630073, Novosibirsk, Russia
2 Kazan State Power Engineering University, Krasnoselskaya st,. 51, 420066, Kazan, Russia
* Corresponding author: email@example.com
There is usually no information about permissible error of current transformers in modes succeed by large relative short-circuit current, at which microprocessor-based protections operate stably. By this reason, it is necessary to use data, defined for analog relays. It leads to value appreciation of a project because it is often essential to reduce current transformers’ error in case of a short circuit fault. Therefore, it is necessary to define the value of current transformers’ error, permitted for impedance relays. Conclusions of fundamental and applied sciences (mathematical analysis, theoretical foundations of electrical engineering, theory of simulation), analytical methods of researching nonlinear circuits and digital signal processing were used. A simulation model was created for setting overall tests of the current trans-former (CT) system. It was a relay protection device that reflected all the important properties of studied objects and allowed an analysis of digital distance protection’s operation at high levels of short-circuit currents. The factors influ-encing over digital distance protection’s operation in case of deep saturation of CTs were revealed, and a certain algorithm for definition of the permissible CT errors was proposed. Stable operation of digital distance protection was observed in case of a fault nearby the place of current transformers’ setting in all theoretically possible combinations of electrical system’s power and length of a protected electric power transmission line. It is valid if electric load choice is carried with account for stable protection’s operation in condition of a fault in the computational point and if voltage swell in secondary wirings is infeasible.
© The Authors, published by EDP Sciences, 2021
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.