E3S Web Conf.
Volume 178, 2020High Speed Turbomachines and Electrical Drives Conference 2020 (HSTED-2020)
|Number of page(s)||4|
|Published online||09 July 2020|
Vibration Diagnostics of Power Equipment Before Commissioning
Sukhoi State Technical University of Gomel, Prospect Octiabria, 48, 246746, Gomel, Republic of Belarus
2 State Enterprise “Research Institute Belgiprotopgaz”, Domashevskij lane, 11a, Minsk, Republic of Belarus
3 Kazan State Power Engineering University, str. Krasnoselskaya, 51, 420066, Kazan, Russia
* Corresponding author: firstname.lastname@example.org
The article describes how to use vibration diagnostics to detect defects in the installation of new equipment and to determine the quality of repairs based on vibroacoustic characteristics. Especially relevant is the vibration diagnostics of rolling bearings before installation on the mechanism. If there are errors in the calculations of the magnetic system of synchronous generators, vibration occurs, which is not eliminated during operation. Design errors, poor assembly of pumping units, asynchronous motors, power transformers cause increased vibration, which leads to damage to the specified equipment. The main reasons causing the vibration of the transformer tank are considered and the frequency range from 50 to 6000 Hz is determined on which these defects can occur. Full-scale experiments of the vibration of the transformer tank have shown that certain defects can occur in a narrow frequency band. The practical application vibration diagnostics of the pump unit describes in this article. Technical diagnosis of pumping units of the sewer station was carried out for various included composition. The results obtained made it possible to exclude reverse hydraulic impacts as a possible cause of the failure of the pump unit.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.